- Everpure EV9437-11 High Flow CSR Quad-MC2 System w/Low Pressure Alarm Features:
- The Everpure HF CSR Quad-MC2 System delivers premium quality water for high flow combination applications such as fountain, coffee and ice machines.
- The CSR Quad MC(2) has a 20" prefilter that captures larger dirt particles.
- The Everpure High Flow CSR Quad-MC2 EV9437-11 filter system with LPA reduces chlorine taste and odor and other offensive contaminants that can adversely affect the taste of beverages.
- The Everpure HF-CSR-Quad-MC(2) combination filter system features new and improved Micro-Pure II media which inhibits the growth of bacteria.
- The Everpure High Flow EV934711 Quad-MC-2 System w/low pressure alarm features precoat submicron technology which reduces dirt and particles as small as 1/2 micron in size and reduces possible health contaminants such as cysts.
- Sanitary cartridge replacement is simple, quick and clean.
- NSF Certified under NSF/ANSI Standards 42 and 53.
- The HF CSR Quad-MC2 includes the SR-X Scale Reduction Feeder with SS-IMF cartridge which inhibits limescale buildup in ice machines and coffee brewers.
- The EV934711 can be used with up to 4 carbonators combined with a 4 pot coffee brewer and 1,200 lb. ice machine.
- Low pressure alarm signals to notify when cartridges need changing.
- The Everguard Low Pressure Alarm (LPA) consists of a pressure switch, audible/visual alarm box and a power adapter. It is designed to detect a fixed low pressure (approx. 20 psi) condition as an indication of loss of system outlet pressure either due to an intentional shut-down or excess fouling of the water filters, thus indicating the need for filter cartridge change-out.
- Everpure HF CSR Quad-MC2 System (w/LPA) Specs:
- Dimensions: 25.69”H x 34”W x 6.75”D
- Inlet/Outlet Connection: 3/4” FPT
- Rated Capacity: 36,000 gallons
- Maximum Service Flow: 6.7 gpm (25.4 Lpm)
- Micron Rating: 0.5 (nominal)
- Temperature: 35°F - 100°F (2°C - 38°C)
- Pressure Requirements: 10 - 125 psi (0.7 – 8.6 bar), non-shock
- Operating Weight: 58 lbs.
- Electrical Connection: 110V Electrical Connection required for low pressure alarm
- Manufacturer: Everpure EV9437-11
- Everpure HighFlow CSR Quad-MC-2 EV9437-11 System replacement filters:
- Everpure EV9612-56 MC-2 replacement cartridges.
- Everpure EV9799-02 SS-10 replacement cartridges.
- We do not sell the Everpure EC210 filter. Instead of this filter purchase the compatible Pentek PD-10-20 sediment filter.
- Everpure EV943711 High Flow CSR Quad-MC(2) System with Low Pressure Alarm Instructions:
- Change cartridges on a regular 6 month preventative maintenance program.
- Change cartridges when capacity is reached or when pressure falls below 10 psi.
- Always flush the filter cartridge at time of installation and cartridge change.
- Flush cartridges by running water through system for five minutes at full flow.
- Change the SS-10 cartridge when product level in the cartridge drops below 1/2" from the bottom of the bowl.
- Change prefilter cartridge when excessively dirty (observed visually or by flow restriction).
- All carbon filter cartridges on multiple cartridge systems should be changed at the same time.
- Fountain equipment connections are made to the outlet part of the system before the SR-X system.
- Coffee brewer and ice machine connections are made after the SR-X feeder; a tee is required.
- Install vertically so cartridges hang down.
- Allow 2-1/2" clearance below the cartridge for easy cartridge replacement.
- Choose a mounting location suitable to support the full weight of the system when operating.
- Allow adequate space for “in” and “out” water line connections. Be near a drain for flushing.
- Use 3/4” water line.
- For installations in Massachusetts, the Commonwealth of Massachusetts Plumbing Code 248 CMR shall be adhered to. Consult your licensed plumber for installation of the system. This system and its installation must comply with state and local regulations.